AUST – HENDRY building surveyors advise that the Building Code of Australia (BCA) under Part G1, Clause G1.2 ‘Refrigerated chambers, strong rooms and vaults’ sets out safety criteria for the safe operation of refrigerated chambers (cool room/ freezers). These provisions are ignored frequently when considering essential safety measures provisions.
Building Compliance System
Through the various types of inspections (such as essential safety measures, BCA audits, due diligence audits or fire safety audits) undertaken by HENDRY and Essential Property Services, our staff become aware of situations in a number of buildings that are unsafe for the occupants of a building.
While essential safety measures legislation concerning the maintenance of essential safety provisions around Australia does not allow for ‘directions’ to be used to force an existing building to comply with the current Building Code of Australia, a statutory authority (in most instances, the local council) can force the owner of an existing building to comply with current regulations (building upgrade), usually via a building notice or similar instrument.
The following photographs depict various situations that don’t comply with the current provisions of the Building Code of Australia under Clause G1.2.
Building Code of Australia
In part, Clause G1.2 states:
G1.2 Refrigerated chambers, strong-rooms and vaults
(a) A refrigerated or cooling chamber, strongroom or vault which is of sufficient size for a person to enter must have –
(i) a door which is capable of being opened by hand from inside without a key; and
(ii) internal lighting controlled only by a switch which is located adjacent to the entrance doorway inside the chamber, strongroom or vault; and
(iii) an indicator lamp positioned outside the chamber, strongroom or vault which is illuminated when the interior lights required by (a)(ii) are switched on; and
(iv) an alarm that is –
(A) located outside but controllable only from within the chamber, strongroom or vault; and
(B) able to achieve a sound pressure level outside the chamber, strongroom or vault of 90 dB(A) when measured 3m from the sounding device.
The building owner and occupier may be at risk to statutory and civil litigation if someone using the refrigerated chamber is unable to escape due to the presence of locking devices impeding the exit path; also an inadequate audible sound system contributes to their injuries or worse. Civil litigation would easily reveal that the refrigerated chamber does not comply to current building compliance (community expectations) when compared with the current Building Code of Australia provisions.
Building Legislation Table