Fire Control Room
A fire control room (fire control centre) is required in a building over 25m in height and if a total floor area exceeds 18,000sqm under the Building Code of Australia (BCA). A building surveyor/ building certifier will nominate a fire control room as an essential safety measure in the statutory essential safety measures schedule required to be issued prior to occupation of the building.
Building Code of Australia
The following part extracts from the Building Code of Australia (BCA) covers the pertinent parts of the BCA clause which govern the fire control room location, protection, contents and maintenance for the issuing of a building approval:
E1.8 Fire control centres
A fire control centre facility in accordance with Specification E1.8 must be provided for –
- a building with an effective height of more than 25 m; and
- a Class 6, 7, 8 or 9 building with a total floor area of more than 18-000 m2.
FIRE CONTROL CENTRES
This Specification describes the construction and content of required fire control centresand fire control rooms. A fire control is a fire control centrein a dedicated room with additional specific requirements. Clauses 2 to 5 apply to fire control centres (including fire control room). Clauses 6 to 12 apply additional requirements to a fire control room.
The following illustration depicts the size and contents of a fire control room.
The following is a part extract of Clause I1.1 for an Essential Safety Measure (as appeared in BCA 2013) known as fire control room:
Table I1.5 SAFETY MEASURES – FIRE FIGHTING SERVICES AND EQUIPMENT
||BCA Provision for Determining Standard of Performance
|Fire control centres (fire control room)