AUST – Essential Property Services advises that some of our essential safety measure fire door inspections and smoke door inspections (under AS 1851-2005 ‘Maintenance of fire protection systems and equipment’) in hotels have identified installed magnetic door hold-open devices to guest rooms. These devices hold open the door for entrance purposes and cleaning. Since these fire doors and smoke doors are required fire doors or smoke doors under previous building approvals issued at the time of construction, a problem exists when the doors are being held open. These doors were required to be self closing upon entry to the room.
In the event of injury or loss of life, these hold open devices will be critically assessed by authorities and the courts as well as insurance companies, especially as they are nominated in the essential safety measures logbook. Managers should validate the installation of these devices on fire doors or smoke doors via a building approval, so they can remain legal (probably with conditions) or consideration should be given for their removal as continual maintenance under AS 1851-1 ‘fire door inspections’ reveals non-compliance on an ongoing basis and may result in a building notice… (more)
Fire Safety Compliance: Essential Safety Measures
For further advice, please contact the Essential Property Services office by clicking here.